Our Datacenter team discover an anomaly on one of the UPS bank and will perform a emergency maintenance.
Power will be transferred to utility power during this maintenance. Once completed, power will be put back on the UPS load.
This will cause your VPS to reboot twice with a small downtime period.
Sorry for the inconvenience,
- Gestion DBI Team.
Related servers / services
|16/08/2019 10:23:00||VPS are now rebooting.|
|16/08/2019 13:30:00||Contractor is ready to switch the load back. Expected time: 14h30 EST. We will shutdown the server around 14h00.|
|16/08/2019 14:03:00||All VPS has been shut off. We will start them after the maintenance.|
|16/08/2019 15:00:00||Power is restored on UPS. We start the server and VPS.|
|16/08/2019 15:06:00||We are unable to restart the server. We are investigating with DC Team on-site.|
|16/08/2019 15:12:00||Problem solved. All VPS are booting. Plan up to 30 min of instability until the node stabilize itself.|
|16/08/2019 15:26:00||Everything is back to normal. We close this event.|